Today we want to share our experience in designing of optimal air circulation and refreshing ventilation. How do you organise your barn ventilation system efficiently? Let's start with the theory.
Cattle are more sensitive to high temperatures. Optimum barn temperatures should be between 0 and +16 degrees. Temperature higher forces the cow to adapt to the environment by triggering a mechanism to regulate heat in the body, or heat dissipation.
The heat transfer process carried out through the skin as well as the respiratory and secretion organs. Heat released through the skin by means of heat conduction (convection), thermal radiation (radiation) and evaporation of moisture. Thermal conduction (convection) is the transfer of energy in the form of heat from a warmer body surface to the surrounding air.
Thermal conduction depends on the ambient air temperature, speed and humidity. Heat radiation - radiation from the skin surface of infrared rays that are absorbed by surrounding objects. Evaporation of moisture from the skin surface of animals is the result of sweating, which consumes a lot of energy in the form of heat.
At high ambient temperatures close to body temperature, the heat output from convection and radiation drastically reduced, and the heat output from evaporation of moisture from the body surface is significantly increased. Accordingly, in order to replenish the moisture, the animal begins to drink abundantly, which leads to a feeling of saturation; the cow eats less feed, gives less milk.
Correspondingly, by directing the air flow to the animal, we contribute to the heat dissipation - we facilitate heat conduction and moisture evaporation from the animal's skin.That's why it's more important to ensure that the room is not just air movement, but air movement directed at animals. It has been established that the movement of air from 2 m/s and above will give the result needed to combat thermal stress.
Thus, the best option for the installation of booster fans is to place them along the lines of the stables with tethered housing or in two rows along the aft table and adjacent boxes with loose housing.
Pay attention to the performance. Fans with a capacity of 40,000 m³/h produce an airflow of 2m/s at a distance of 12m. At a distance of 18m the speed will be about 1-0,9 m/s. The airflow width of such fans is about 4m. A decrease in the fan capacity will mean a reduction in the length of the airflow. Thus, a fan with a capacity of 20,000 m³/h will create an effective flow length of 2m/s at a distance of no more than 6m, and the flow width is less than approximately 2 times. It is recommended to install these fans only in case it is not possible to install larger ones. The fans should be installed at the height of 2,7 m from the floor, at an angle of 12-14°.
The effect of accelerating ventilation is most noticeable for highly productive animals (with milk yield per cow from 20 kg). The result of the conditions described above will be an increase in milk yield by 10% and more.
For many years, the agent has been supplying overclocking fans to EkoNiva's farms. In addition to reducing heat stress in animals, the installation of fans has reduced the seasonality of milk production in summer and increased milk yield by 3 liters per cow.
We've got a couple of fans hanging, we haven't noticed the effect of them. The effect will only come from standardization when you create air movement along the entire length of the animal housing section. Pay attention! If your fan is angled (towards the cows) the animals will try to get into the air movement area.
It is better to put the overclocking fans along the feeding table to blow the exhaust air through the gate. It is inefficient to use the overclocking fans to solve this problem. They will not contribute to reducing thermal stress. In order to remove the exhaust air, it is more efficient to install several exhaust fans that will blow the exhaust air outwards.
Ceiling fans are better. The function of ceiling fans is to stir large air masses rather than to blow animals in a directed manner. Ceiling fans should be installed for operation during the cold season, when the mixing of air in the farm premises will equalize the temperature. The fans raise the used (polluted) air upwards, mixing it with the incoming cold air, reducing the humidity level and making it easier to remove it from the room.
In conclusion, it should be noted that the installation of an overclocking ventilation system is the first step towards combating the heat stress of animals. In order to make the overclocking ventilation more efficient, we recommend the installation of mist elimination systems. More information about misting systems can be found in the following material.
Keep an eye on updates!
Как повысить эффективность микроклимата в коровнике? Принципы организации вентиляции в коровнике «советского типа». Как бороться c тепловым стрессом у КРС?
Мы начинаем серию публикаций материала об организации микроклимата в помещении животноводческой фермы
Датчики влажности, углекислого газа, давления и корма от производителя, всегда в наличии!